Have a Question? 502-859-5490
My Items of Interest
Western Reserve Controls
Sensor / IO Inputs
> Point Sensor Power Monitor
Point Sensor Power Monitor
Point Sensor Power Monitor
Minimum Order Quantity 200 Pieces
25 - 99
Add to Cart
•Measures current draw up to 40 Amps
•Compatible with AC circuits
•64-Bit unique ID
•12-bit analog to digital conversion
•Transmits unique ID and analog value
•Up to 600 foot transmission range
•Transmission intervals from 10 to 17 seconds random
•Patent pending modulator
•Battery life up to 5 years
•Very small (1.3” X 2.1” X .6”) ABS enclosure
•Water resistant coating on PCB
•Internal loop antenna
3005-56 - Point Sensor Power Monitor, 418 MHz
5002-09-A5-3005-122 - Point Sensor Power Monitor, 433 MHz
The Point Sensor Power Monitor wireless transmitter is a battery operated 12 bit analog-to-digital converter with a microprocessor controlled 418 MHz or 433 MHz. FCC certified radio transmitter. The Sensor has an on board time of day clock that allows it to spend most of the time in a low power quiescent state. At predetermined time intervals the clock will wake up the onboard microprocessor. Unique serial number information is read from a Dallas Semiconductor 1-wire digital device and analog data is read from a 12-bit analog to digital converter. This information is combined with a CRC-16 error check and transmitted in a very short data packet that results in a transmitter on time of only 15 milliseconds. This architecture allows the Sensor to consume very low energy resulting in a battery life of up to 5 years.
The electronics are coated with a conformal material that provides a moisture barrier against condensation. Submersion in water is not recommended. An integral pushbutton is used to activate the service switch. The Sensor is shipped with the transmitter turned off (anytime the Sensor is to be shipped the transmitter should be turned off or must be placed in a shielded container to prevent interference that might cause shipping problems). Start the Sensor by momentarily pushing the service switch (you will feel the button click). When the service switch is pushed a data transmission occurs immediately and a special mark is introduced in the ID field of the transmitted data packet to indicate which sensor is in service or installation. The service switch is also used to put the Sensor in a quiescent mode (no transmissions and very low power consumption). This is the state the Sensor is in when you receive it from the manufacturer. Push and hold the service switch for 5 seconds or more to enter this powered down state.
Was this answer helpful?
[a_helpful] of [a_votes]
Customer(s) found this Answer helpful.
Answer provided by:
No Answers have been submitted yet.
418 MHz or 433 MHz
10-17 seconds random
FCC ID: M5ZANA
Shelf life with battery installed
5 Years in quiescent mode (10 years with optional battery)
1.5 W X 2.1 H X .6 D (inches)
0% to 90% non-condensing
Up to 600'
-40°C to 85°C
2-5 years with tx period of 10-17 seconds
Point Sensor Power Monitor Spec Sheet
Point Repeater 4.9.9
Point Sensor Analog
Universal Output Module
Browse By Category